44 timestamp and quality in CDC TMS is missing for dly, mly and yly (like CDC CTE)
This tissue has following status: white
Created: 11 Nov 2016
Paragraph: Table 42
Category: Issue for edition 2 of this part
Issue: There is no timestamp and quality information for the state timing dly, mly and yly state timing counter in the CDC TMS available. The CDC CTE got this information in editon 2 by using the complete CDC BCR for the dly, mly and yly information.
Proposal: Change the type of the ARRAY from INT32U to a CDC e.g. BCR as it is done in CDC CTE.